- Los Angeles, CA
Dietetics Building – Los Angeles
Scope of Work
- Provide installation of a new overhead fire sprinkler system throughout proposed VA Building, as shown on provided plans and specifications.
- Building construction is type IIB & approximately 28,000 ft.2 in total area floor area. Systems to comply with the City of Ventura Fire Department as well as NFPA-13, 2019 requirements for B, S-2, F-1 occupancies.
- Provide Freezer sprinkler heads in cooler areas.
- Sprinkler coverage will be provided throughout structure. Heads will be spaced for ordinary & light occupancies.
- Fire sprinkler spacing to be a maximum of 130 sq. ft. & 225 sq. ft. in light hazard areas.
- Precision Fire’s point of connection to be 6” above finished grade.
- Includes Risers, Mains, Drops, Hanger & Seismic Bracing.
- Fire sprinkler riser to include electronic flow switch, and electronic 10-inch fire bell (installation of bell by others & wiring to bell and flow switch also to be done by others)
- Fire sprinklers in new scope of work to be new quick response per NFPA 13 2019.
- All above ground piping shall be but not limited to steel sch. 7, 10, 30 & 40 with threaded and/or Victaulic grooved/mechanical fittings.
- Work shall include all materials, labor, plans, design calculations, shop drawings, design coordination meetings, plan submittal, rough & final fire sprinkler inspections.
- Design-Build Engineering will be provided for this project.
- Copies of Permits & Approved Fire Sprinkler Plans to be provided to Client upon request.
Loading next items...